Consideration of appropriate safety criteria (usually an allowable shock voltage) is required for all #electrical assets that form part of the #network. Consideration should be made for #substations (both inside and outside) and for the accessible portions of the #powerlines and cables.
The specific locations will represent a different #risk profile by virtue of the fact that there will be different coincident probabilities of system events and human contacts and different series #impedance (for example, footwear and surface coverings).
Consideration should be given to factors such as:
Probability of multiple simultaneous human contacts (particularly in public places), (i.e. touch, step, hand-to-hand or transfer voltage impacts)
Susceptible locations (wet areas)
Controlled access areas (fenced easements or remote areas)
Series impedance (surface coverings and footwear)
Future possible encroachments upon the electrical network and the effect of system events on those encroachments
Conductive and inductive coupling into non-power system plants such as communications infrastructure, telecoms, pipelines and conveyors.
The figure below summarises the main risk elements in each category.
Some external factors that need to be addressed (during design and installation) are theft and/or vandalism of earth system components. Consideration should be given to protecting exposed components and/or monitoring key components to ensure an acceptable risk profile
All life activities involve some form of inherent risk. The tolerability of injury or death to a member of the public is therefore dependent upon several factors including the types of hazards, the control measures implemented, #frequency of occurrence, the likelihood of actions of the individual(s) exposed and the associated consequences.
!!! Risk in this context is defined as ‘the chance of something happening that will have an impact on objectives‘ (i.e. a combination of the consequences of an event and their likelihood, frequency or probability).
The risk associated with a hazard is determined using a risk assessment process in which #hazards are identified, analysed using quantitative #methods and qualitatively assessed against specific criteria.
Once the risks are evaluated, the appropriate risk treatment process shall be implemented where appropriate to effectively and efficiently manage the risks.